Plasma Generator DLZ-MA-300D of Plasma Ignition System
1.Cathode conduit，2. Arc striking mechanism，3. Hood，4. Anode bearing assembly，5. Arc striking anode，6. Transition anode assembly，7. Main anode
Outline of generator DLZ-MA-300D
Anode bearing assembly:It is the platform of installation for other parts,like anode, cathode, arc striking mechanism. Besides, it can introduce and distribute the cooling water and medium air with corresponding connections on it, as shown in Figure 3.3 in detail.
Arc striking anode: Its arc striking cone contacts with the cathode head, and then the cathode head moves backward to complete plasma arc striking and the generator’s start-up. After that, this anode acts as the arc channel to compress the arc for the first stage.
Transition anode assembly: After the arc striking is completed and the voltage reaches the normal value, the transition anode acts as the arc channel, organizes the air flow to compress the arc for the second stage, and pushes forward the anode arc root to ensure it falls on the main anode.
Main anode: When the generator works, the arc root of the anode falls on the inner surface of main anode, and the plasma jet is ejected from its nozzle. The main anode will be damaged due to high temperature ablation during operation until it is burnt out. It needs to be checked and replaced regularly.
Cathode conduit: As shown in Figure3.7, the cathode gun is mainly composed of cathode head, body, cathode end set. During operation, the cathode head is damaged by high-temperature radiation heat and positive ion bombardment, and needs to be replaced regularly. The incoming and returning water connections on the cathode end set are respectively connected to the incoming and returning water joints on the anode support assembly to cool the cathode head.
Arc striking mechanism: It includes a motor, a pulling rod and a hook. The pulling rod drives the cathode gun forward through the hook and contacts with the anode. After the arc striking current is established and stabilized, pull the cathode backward to complete the generator start-up. See Figure 3.8.
Incoming water pressure: 0.6~1.0MPa
Water pressure difference between inlet and outlet: 0.4MPa~0.8MPa
Compressed air parameters
|First stage air||Second stage air||Working current